The phase identification system PIL8 permits a fast and especially safe phase determination at the jointing location during the mounting of medium voltage cables.
According to DIN VDE 0105 0100 part 2 (EN 50110-1) from Oct. 1997, Pos. 184.108.40.206 Topic 3 (Page 12) it specifies :
“… If the earthing or shorting has to be removed for the duration of measurements or tests, suitable other safety measures have to be taken.”
Such safety measures take a lot of effort and are not always practical. PIL 8 requires that the ground or shorting must not be removed. On the contrary, this grounding is an essential part of the procedure, which means, the cable must be grounded and shorted for the system to work with the result that test is absolutely safe. For each phase the corresponding transceiver clamp is installed on the grounded cable end and then at the selection point each phase is identified and marked.